750.0300 EC IL JS LS TS Series Installation Directions
: Pdf 647591-Installationsheet 647591-InstallationSheet 782683 Batch5 unilog
Open the PDF directly: View PDF .
Page Count: 1
|Open PDF In Browser||View PDF|
EC/IL/JS/LS/TS Series EC/IL/JS/LS/TS Series IMPORTANT SAFEGUARDS 4. Extend DC wiring for remote fixtures, (if required), to unit. Wiring must comply with NEC articles 700 and 720. Do not exceed rated wattage of unit. 5. When ready to energize AC, plug polarized battery connector into circuit board. Lamps will not light at this time. 6. Energize AC. Pilot lamp and high charge LED will illuminate. 7. For conduit installation on the JS series, use 7/8’’ knockout located on the top of the enclosure. When using electrical equipment, basic safety precautions should always be followed including the following: Testing READ AND FOLLOW ALL SAFETY INSTRUCTIONS (See separate booklet for units with AD option) Allow one minute for unit to stabilize before testing. To test, depress test switch. Pilot lights will go out and emergency lamps will come on. When test switch is release, emergency lamps will go off and both pilot lights will come on. Allow a minimum of 24 hours charge time after installation or power failure for initial full load testing. WARNING: Risk of Shock. Disconnect Power before Installation. 1. All servicing should be performed by qualified service person2. 3. 4. 5. 6. nel. Maintenance Do not use outdoors. None required. Unit should be tested monthly in accordance with the requirements of NFPA 101, Life Safety Code, or local codes. Do not let power supply cords touch hot surfaces. Do not mount near gas or electric heaters. Use caution when handling batteries. Avoid possible shorting. Equipment should be mounted in locations and at heights where it will not readily be subjected to tampering by unauthorized personnel. 7. The use of accessory equipment not recommended by the manufacturer may cause an unsafe condition. 8. Caution: If optional Halogen cycle lamp(s), symbol (H—), are used in this equipment, to avoid shattering: do not operate lamp in excess of rated voltage, protect lamp against abrasion and scratches and against liquids when lamp is operating, dispose of lamp with care. Important notice This equipment is furnished with a low battery disconnect circuit in the emergency mode. If the building is to be unoccupied for an extended period of time and all the power is to be disconnected, the internal batteries must be unplugged from the circuit board to prevent damage. Do not allow the battery wires to short circuit. WARNING: Risk of serious injury. To prevent injury from falling battery, carefully hold batteries in place when removing and re-installing the securement bracket. Take special care for ceiling mount configuration. 9. Halogen cycle lamps operate at high temperatures. Do not store or place flammable materials near lamp. Note : Select proper input wire and insulate unused transformer lead Note: Secure AC wires via wire clip after making connections. 10. Do not use this equipment for other than intended use. Wiring to be done in this area AC input SAVE THESE INSTRUCTIONS Lamps White Black (120) Installation Orange (277) 1. TURN OFF AC POWER. 2. Route AC circuit wires to electrical box and leave 12’’ of wire length. 3. Securely mount unit in place. Connect AC supply wiring to unit as follows: For 120 VAC operation : — Black to 120 VAC, White to neutral * For 277 VAC operation : — Orange to 277 VAC, White to neutral * Unused primary wire must be insulated to prevent shorting. NOTE: Secure AC wires via wire clip after making connections. Circuit board IMPORTANT: Wiring connections need to be done away from PCBA and in designated area as shown in figure below. Emergi-Lite Tel: (888) 552-6467 Fax: (800) 316-4515 Battery connector Battery *Unused primary wire must be insulated to prevent shorting. www.emergi-lite.com 03/14 750.0300 Rev. I 1/1
Source Exif Data:
File Type : PDF File Type Extension : pdf MIME Type : application/pdf PDF Version : 1.5 Linearized : Yes Author : CADOERM Create Date : 2014:04:28 10:02:28-04:00 Modify Date : 2014:04:28 10:02:28-04:00 XMP Toolkit : Adobe XMP Core 5.2-c001 63.139439, 2010/09/27-13:37:26 Creator Tool : PScript5.dll Version 5.2.2 Format : application/pdf Title : 750.0300-EC-IL-JS-LS-TS series.fm Creator : CADOERM Producer : Acrobat Distiller 10.1.9 (Windows) Document ID : uuid:7c61beb3-1737-47c5-baa4-c8d5c79d26db Instance ID : uuid:b2f5d279-91c3-400e-966c-16a7a1cfb8f4 Page Count : 1EXIF Metadata provided by EXIF.tools